In the kitchen there are high temprature and flammable oils because of this reason kitchens are one of the places where there is a constant risk of fire. The oil carried by the steam removed from the environment by the operation of the ventilation system accumulates in the hood, plenum and ventilation ducts. A fire occurs in filters, ducts or equipment (oven, fryer, grill, etc.).
Electricity and gas lines increase the risk of fire in kitchens. In case of fire, electricity and gas inlets should be closed. The fire is prevented from growing, lowering the extinguishing load and reignition.
we designed and installed automatic fire extinguisher system in and under hood. Possible hood fire risks are taken into consideration and protection is provided.
In accordance with the Regulation on Fire Protection of Buildings; Except for residences, it is essential to establish an automatic extinguishing system in the hoods of shopping centers, kitchens and food factories located in high-rise buildings and kitchens that serve more than 100 people at the same time, and install gas detection, gas cutting and warning installations according to the characteristics of the gas used in the furnaces.
Automatic hood extinguishing systems; shopping malls, factories, hospitals, hotels, restaurants,… etc. used in the kitchens. It detects the fire in a very short time and extinguishes it with the least damage in the hood fires that may occur, especially in the absence of people in the kitchens. When it is ensured that the surface has cooled down after the fire, it should be cleaned. It can be cleaned with warm soapy water and sponge.
Heat sensitive fusible type detectors are used for every cooking equipment and in every ducts or in the hood with 60cm intervals and in every ducts. These detectors contain heat-sensing fusible link. When it detects heat, it enables the system to operate automatically. The system performs the detection and extinguishing function automatically, and the system can be operated manually with the manual pull and discharge button. Pull buttons allow manual operation of the system in case of fire. The buttons should be placed on the escape route and in easy-to-reach places.
- System Control Unit:
- System pipe installation
- Cylinder (Potassium Carbonate)
- Manual Discharge Button
- Fusible detectors
- Normally closed
- Corner reels and accessories